Whole house water filter for Iron, Magnesium Treatment
Birm® is an efficient and economical media for the reduction of dissolved iron and manganese compounds from raw water supplies. It may be used in either gravity fed or pressurized water treatment systems.
Birm acts as an insoluble catalyst to enhance the reaction between dissolved oxygen (D.O.) and the iron compounds. In ground waters the dissolved iron is usually in the ferrous bicarbonate state due to the excess of free carbon dioxide and is not filterable. Birm, acting as a catalyst between the oxygen and the soluble iron compounds, enhances the oxidation reaction of iron and produces ferric hydroxide which makes the iron combine into sediment particles and may be easily filtered.
The physical characteristics of Birm provide an excellent filter media which is easily cleaned by backwashing to remove the precipitant. Birm is not consumed in the iron removal operation and therefore offers a tremendous economic advantage over many other iron removal methods.
Other advantages of Birm include:
long material life with relatively low attrition loss
A wide temperature performance range and extremely high removal efficiency.
Negligible labor costs are involved because Birm does not require chemicals for regeneration, only periodic backwashing is required.
When using Birm for iron removal, it is necessary that the water:
Contain no oil or hydrogen sulfide
organic matter not to exceed 4-5 ppm
The Dissolved Oxygen content equal at least 15% of the Iron content
A pH of 6.8 or more.
If the influent water has a pH of less that 6.8, neutralizing additives such as Clack Corosex®, Calcite or soda ash may be used prior to the Birm filter to raise the pH. A water having a low D.O. level may be pretreated by aeration.
Additions of chemicals to influent or backwash water which contacts Birm media may inhibit iron or manganese removal or may break down or coat Birm media. Chlorination greatly reduces Birmís activity. High concentrations of chlorine compounds may deplete the catalytic coating.
Polyphosphates are known to coat Birm and reduce Birmís ability to remove iron or manganese. Before adding any chemical to the influent or backwash water, the chemical's compatibility with Birm should be thoroughly tested.
Clack Birm may also be used for manganese reduction with the same dependability as iron removal. In these applications the water to be treated should have a pH of 8.0-9.0 for best results. If the water also contains iron, the pH should be below 8.5. High pH conditions may cause the formulation of colloidal iron which is very difficult to filter out. All other conditions remain the same for either manganese or iron removal.FRP Tank 1054 10"x54"1.5 CU FT BirmAQT-56FT Backwash TImer ValveIron & Magnesium Treatment